AC and DC Capacitors Should be Replaced?
While most all UPS system users are aware of the fact that the batteries they use for backup power wear out, they are not necessarily aware of the fact that these same UPS also utilize large banks of capacitors as well. These capacitors are used in both the DC (electrolytic capacitors) and AC (polymeric film capacitors) sections of the UPS for filtering. These capacitors age and degrade and need to be replaced before they reach failure mode.
DC Capacitors: These are used to ‘smooth’ the DC link battery charging current as it is drawn from the UPS rectifier. With time their effectiveness is reduced (they wear out) and if not replaced they will eventually fail.
AC Capacitors: These are used to filter either the reflected harmonic current of the UPS rectifier back into the input distribution (Input Filter Capacitors) or to help shape the inverter output so that the wave form is sinusoidal. As with the DC Capacitors, with time their effectiveness is reduced and if not replaced they will eventually fail.
Capacitor Failure: Over time both AC and DC capacitors age, suffering from a deterioration of materials due to usage as well as from ambient conditions such as heat internal to the UPS module. A result is that they become less effective and start to fail. As capacitors fail in a ‘capacitor bank’, those that remain must work harder and as a result they too start to fail. When the caps fail they typical ‘pop’ a safety valve and can start to leak oil, in extreme cases they can rupture.
Experience has shown that AC and DC capacitors should be replaced, just like batteries before they fail, typically every 5 years, and some cases a little more frequently.
Jantech Services has been working with UPS systems for more than 25 years, and has both the experience, and the necessary capacitors you need available when you need it.
Find out more about our UPS Maintenance Options
Follow us on Twitter for updates and helpful tips
When you think of spring cleaning, don’t forget your UPS has air filters that also need to be changed, typically no less than 6 months and as often as every month depending upon the local environment.
Be sure to check out our latest White Paper OLDER UPS, NEWER IT LOADS
Jantech Services – www.JantechUPS.com – 1800.452.6832 – web@JantechUPS.com
Southeast*: 11315 Challenger Ave, Odessa, FL 33556
Mid Atlantic: 2821 Rowland Rd, Raleigh, NC 27615
NY Metro: 333 S. 1St Street, Bangor, PA 18013
Northeast: 119 E Central St, Suite C, Franklin, MA 02038